The ability to safely tie-in to a pressurized system while under full operating
Hot Taps can be performed on most any type of pipe, ranging from carbon steel
to PVC. Taps are done on lines containing water, oil, gases, fuels, steam, and
many other chemicals. Pressures up to 1440 psig at 100º can be Hot Tapped safely
with no interruption of service.
- Stainless Steel
- Steel Cylinder
- Carbon Steel
- Ductile Iron
- Cast Iron
- Crude Oil
- Natural Gas
Koppl Pipeline Services uses the latest technology in coupon retention available. When a Hot
Tap is performed, the double wired pilot drill retains the coupon and it is
recovered when the Hot Tap is completed. (Figure 1 - Left Picture)
Typical Hot Tap installation consists of a tapping saddle, gate valve, and
Hot Tapping Machine. The installation is tested, the valve is opened, and the
cutter and pilot drill advanced. When the cut is completed, the cutter and pilot
drill are retracted, the valve is closed and the Hot Tap Machine removed.
(Figure 2 - Right Picture)
Adding new connections to your piping is not the only use for Hot
Taps. Some of the many uses include:
- Product Sampling Point
- Flow Meter Installation
- Thermo-well Sensor Installation
- Draining of pipelines
- Pressure Control Switch Installation
- Inspection of a pipeline
- Determine product in a pipeline
- Air Relief Point
Koppl Pipeline Services has the ability to tie into your system in many different ways. Angle
taps, valveless connections, long travel taps, and other methods are available
to complete your connection in the most efficient manner possible.
This is the typical configuration for a Hot Tap performed at an angle. An
angle block is used as a guide for our pilot drill and is welded dead center of
the tapping outlet. (Figure 1- Left Picture)
Side Out Fitting installation. This fitting is used when valves are not
required at the point of connection. A temporary valve is used to make the Hot
Tap, then removed. All this accomplished with no interruption of service.
(Figure 2 - Middle Picture)
Hot Taps are being used for a bypass connection during a line stop operation.
Flow continues in the pipeline while necessary modifications are made.
(Figure 3 - Right Picture)
Hot Tapping is the ability to safely tie into a pressurized system while it
is on stream and under pressure. Typical connections consist of a tapping
fitting, isolation valve, and hot tapping machine. (Figure 1 - Left
The hole saw is advanced through the valve, to the pipe. The machine is
engaged and the cut begins. When the cut is finished, the machine is disengaged
and retracted beyond the gate of the valve. The valve is closed and the machine
The coupon is retained by using a wired pilot drill. The wire on the pilot
toggles, thus catching the coupon and preventing it from falling off.
(Figure 2 - Middle Picture)
Elbow taps, angle taps, and taps perpendicular to the pipe are all feasible
means of connecting to your existing pipeline system. (Figure 3 - Right
STANDARD CUTTER SIZES FOR HOT TAPPING
Listed below are the standard cutter sizes used when performing hot taps.
This list is meant for reference only and does not reflect the actual size used
on any particular hot tap. Various conditions will determine the size necessary
to complete the hot tap successfully. If a certain cutter size is required,
please specify that size when ordering your hot tap.
Nominal Hot Tap Size
Nominal Cutter Size
DIMENSIONS REQUIRED FOR HOT TAPPING
- 14 feet for 10” and larger hot taps
- 7 feet for 4”, 6”, and 8” hot taps
- 4 feet for 3” and smaller hot taps
Koppl Pipeline Services maintains a large inventory of equipment that includes hot tapping
machines of different sizes. If the above dimensions do not suit your needs,
please contact your local Koppl Pipeline Services representative. A jobsite visit can be scheduled
to determine the best method of completing your hot tap at your particular
Download Our Hot Tapping Brochure [pdf - 770kb]